Dietrich Idaho Water Project 06-29-2014. Pump #2 running as lead.
06-29-2014 Dietrich Idaho Water Project. Pump #2 running as lead.
1:30-3:30: Opened end hydrant, pump #2 kicked on acting as lead pump, chlorine
pump was running as pump #2 pumped to waste for ten minutes, plc interface read
240 gpm for pump #2 the same as the meter, the plc interface showed pump #1
flowing 270 gpm with the pump off, when the system reached low water condition
the alarm sounded, and the prelube valve opened for pump #1, when this happened
the red dot representing the prelube valve on the plc interface turned green,
after ten minutes when pump #1 started the green dot representing the prelube
valve on the plc interface turned red even though the prelube valve was open
and flowing water, the flow for pump #1 was about 265 gpm on both the meter and
the plc interface.