Dietrich Idaho Water Project 07-17-2014. Well meters output range 4 to 20 mA.
07-17-2014 Dietrich Idaho Water Project. Well meters output range 4 to 20 mA.
Jake Claridge of Extreme Excavation checking to see if analog output on well
house Badger M2000 meter totalizers are set at 4 to 20 mA
excerpt from 07/17/2014 Justin Walker punchlist created after conference call
with Randy Satterwhite of ProWest engineering and Extreme Excavation:
i. PLC and flow meter calibration still not
accurate at low flows. When Pump #1 is off, PLC shows flow of 275+ GPM (see
email from Tom Young dated 6/27/2014 and 6/29/2014) --Jake to get range/scale
of the output 4-20 mA signal from the flow meter; Justin to call IDWR to make
sure they did not tamper with the meter when performing their field check